Adjustment and installation of the RDM-5 pressure switch: instruction, recommendations. One of the ways to control an autonomous water supply is to connect a pressure switch model RDM 5 to a water pump, although the installation and adjustment process in the instructions is not entirely clear, which causes difficulties for users.
At the same time, this type of device from Jileks is considered the most affordable and reliable. The problem of setting and adjusting the RDM 5 pressure switch can be solved if you study the detailed instructions described below.
In private houses without running water, the question of how to provide yourself with water can be solved in two ways:
In the second option, water will be supplied to the house using a pump of the required power. But the fact is that the value of the water pressure during operation is too high to connect the pump directly to the internal water supply network. For this reason, a container with a hydraulic accumulator must be installed in the house, and the required pressure for supply will be maintained by the relay. This device makes it possible to automate the process of water supply in autonomous water supply systems.
The device has a brass body with a special fitting for connecting to the water supply network, electrical relay and spring valves. Outside, the elements are covered with a plastic cover.
The scheme of operation is as follows:
When the pressure in the accumulator is less than the minimum limit, the contacts are closed, and the pump begins to pump water into the membrane intermediate tank.
Usually, ready-made pumping stations are included with the RDM 5 device, which consist of a tank, a pump, a battery (water) and its own control relay.
At the time of purchase, the station will be factory-set and ready to go, but it will first require piping / electrical connection and installation.
But finished products may not fit for a number of reasons:
In these cases, the automatic feeding system will have to be assembled with your own hands from individual elements, and the pressure switch must be set up so that the work is coordinated with the storage tank.
Before purchasing and connecting, we advise you to study all the technical characteristics:
If one of the characteristics does not suit you, then you will have to look for other regulators. But as practice shows, the parameters of the device meet all the requirements of 80% of all autonomous systems.
As mentioned earlier, the installation of the pressure switch RDM-5 is carried out immediately to both systems - water supply and electricity. Installation is carried out permanently, since there is no need to move the device.
In order to connect the pressure switch, it is not necessary to have a dedicated line, but still desirable - so there will be more chances that the device will work longer. There must be a cable from the shield with a solid copper core, which has a cross section of at least 2.5 mm 2 . It is advisable to install a difavtomat or a machine + RCD in a bundle. The parameters should be selected according to the current and largely depend on the characteristics of the pump, since the relay has low power consumption.
Grounding must be present in the circuit, since the combination of electricity and water will increase the risks.
Lead the cables into the special glands located on the back of the case. You will find a terminal block under the cover. It will have 3 pairs of contacts:
e.f. terminals " Line " - required in order to connect the neutral and phase wires from the shield.
There is nothing unusual when connecting - the conductors will need to be protected with insulation, tightened with a clamping bolt.
Check if the conductor is firmly clamped. After half an hour or an hour, you can tighten the bolts, because a material such as copper is quite plastic and the contact can weaken.
There are various ways to install the RDM 5 pressure switch to the water supply system. The simplest option would be to install a special adapter with all the pins. The same system can be assembled from other types of fittings, but the finished version is easier to use.
In such a scheme, at high flow rates, water will enter the system directly and bypass the accumulator. It will start filling after the taps throughout the house are closed.
Adjustment of the pressure switch RDM 5 is performed only after installation and connections to the pipeline and electricity. The connections of indoor and outdoor pipelines must be tested so that leaks that may appear later do not interfere with the adjustment. Due to the fact that the joints are leaking, the pressure can begin to decrease by itself, and this will affect the operation of the device.
Before starting the adjustment, determine the required head. To supply water at all points of the tap, which is located on different floors, it is required to maintain the required pressure in the membrane. The efforts of the tank accumulator must be sufficient to push the entire volume of water to the required height and overcome resistance. For home conditions, the pressure value will have to be determined only by experiments.
The calculation is easy: 1 meter of lift will be equal to 10 meters of the horizontal section and have a pressure of 0.
1 bar. The furthest branch of the water supply should be taken into account. When you roughly determine the head, you need to create this pressure from the side of the accumulator air chamber. To do this, remove the plastic cap from the spool, which is usually located at the end of the tank and, using a conventional pump for a car, pump the chamber, while controlling the pressure with a pressure gauge.
Next is the adjustment according to the instructions:
.. At the same time, you can check the tightness of the external pipeline.
The lower limit must be adjusted so that its value is 0.2 bar higher than that pumped into the accumulator.
As a result, the difference between the upper and lower limits will be at least 1 bar.
As practice shows, the optimal differential is 1.5 bar and then the pump will not turn on too often. After adjustment, you do not need to immediately put the cover back in place, first you need to monitor the operation of the system during the day, since there is a possibility that adjustment will be required.
( 1 grade, average 2 of 5 )
Posted By: Work Style |08, Nov 2020
Posted By: Work Style |12, Nov 2020
Posted By: Work Style |01, Nov 2020
Posted By: Work Style |12, Nov 2020
Posted By: Work Style |13, Nov 2020